According to NFPA’s standards, the location of fire extinguishers housed inside cabinets must be “marked conspicuously.” Also, in large rooms and in places where visual obstructions exist, “means shall be provided to indicate the extinguisher location.” Local building codes typically follow NFPA standards.
Are fire extinguisher cabinets required to be labeled?
NFPA 10 does not specify how the fire extinguisher cabinet is to be marked, but it must be marked conspicuously. A 3-deminsional arrow (tent-card style) certainly meets this requirement, but other types of markings do as well, such as painting all extinguisher cabinets red.
How do you label a fire extinguisher?
Dry Chemical Extinguishers come in a variety of types. You may see them labeled: “DC” short for “dry chemical” • “ABC” indicating that they are designed to extinguish class A, B and C fires, or • “BC” indicating that they are designed to extinguish class B and C fires.
What signage is used to indicate where fire extinguishers are located?
The Fire Chevron Safety Sign is used to indicate to all where the Fire Extinguisher can be located in the event of a fire.
Are signs required for fire extinguishers?
Federal OSHA regulation 1910.157(c(1) only require extinguishers be “identified”. … Therefore, it is usually best to install a sign (or other means of identification) above a portable fire extinguisher so its location can be identified from a distance in case it is obstructed from view.
Do fire extinguishers need to be hung?
Fire extinguishers need to be mounted to the wall so that they are secure, visible, and readily accessible. It is also important to mount them in such a way that they cannot be easily moved or damaged.
What do numbers on fire extinguishers mean?
The number indicates the relative size of the extinguisher, and the letter indicates the type of fire it will extinguish. … On Type A extinguishers, the number relates to how many gallons of water the extinguisher is equal to for a Type A fire. Type B fires are of flammable liquids such as gasoline or oil.
What is the OSHA standard for fire extinguishers?
NFPA recommends one 2-A fire extinguisher for every 3,000 square feet. OSHA requires employees to have access to an extinguisher within 75 feet. Employees should have access to a fire extinguisher within either 30 or 50 feet, depending on the hazard in question and the rating of the extinguisher (see below).
What color should walkway lines be?
It specifies that red and yellow must be used for marking physical hazards. Red identifies fire-related hazards (including fire protection equipment and containers of flammable liquids), as well as emergency switches, bars, and buttons on hazardous machines.